Email
 Windmills Forum Index : Windmills         Section -- Select Forum -- Off grid living and renewables   - Windmills   - Solar   - EV's Electronics and Microcontrollers   - Electronics   - Microcontroller and PC projects   - PCB Manufacturing Miscellaneous   - Other Stuff   - Site News   - Off topic archive. Classifieds   - Price Watch   - Wanted   - For Sale Guest Book   - Guest Book
 Topic: Cable/Wire sizing AC/DC
Author
 Message << Prev Topic | Next Topic >>
BarkyJ
Senior Member

Joined: 26 April 2018
Location: New Zealand
Online Status: Offline
Posts: 114
 Posted: 11 May 2018 at 10:28am | IP Logged
Hi All

Just doing some planning.
What is typically done for power cable from the windmill to whatever interface you guys use, and do you normally run 3 phase AC down the pole and rectify it at the ground, or rectify it on the windmill and run DC down the pole?

I found a good youtube clip which has an attached excel sheet for doing calculations which is quite useful.

Based on this, my estimation whether I run AC or DC down the pole, I am in the region of requiring AWG 8 cable, which isnt cheap stuff.
My estimation so far is 15m one way, so 30m of cable (assuming DC 2 wire).

Curious what others are using and where you sourced the cable from.

Thanks

BarkyJ
Senior Member

Joined: 26 April 2018
Location: New Zealand
Online Status: Offline
Posts: 114
 Posted: 11 May 2018 at 11:40am | IP Logged
http://www.nzev.co.nz/10mm-flexible-cable/

This is what I am currently looking at.

Warpspeed
Guru

Joined: 09 August 2007
Location: Australia
Online Status: Offline
Posts: 1974
 Posted: 12 May 2018 at 10:42am | IP Logged
You do not say what your system voltage is, or the expected current.

Ten mm squared cable has a resistance of .00172 ohms per linear meter, so 30m of that cable will have a resistance of .0516 ohms (at 20 Celsius).

The "normal" current rating for 10mm cable is 50 amps.
I squared R gives a power loss of 129 watts at 50 amps for 30m of cable.
Voltage drop at 50 amps would be 2.58 volts.

I have no idea if those are significant figures for your intended application.

__________________
Cheers, Tony.

BarkyJ
Senior Member

Joined: 26 April 2018
Location: New Zealand
Online Status: Offline
Posts: 114
 Posted: 12 May 2018 at 3:03pm | IP Logged
Sorry the system voltage at this stage is 36V.

Warpspeed
Guru

Joined: 09 August 2007
Location: Australia
Online Status: Offline
Posts: 1974
 Posted: 12 May 2018 at 4:16pm | IP Logged
So its going to have about 7% loss at 50 amps.

__________________
Cheers, Tony.

If you wish to post a reply to this topic you must first login
If you are not already registered you must first register